Whether you're a phone service provider, internet service provider, or some other type of telecommunications company, it's your responsibility to ensure that your communication services are always operating correctly for your customers.
Network downtime will cause a whole list of problems, and all of them can be very costly. You can even face fines for every minute of the network outage. If your network is down for longer than a few minutes, you can be facing a lot of money in fines, penalties, or SLA refunds.
Network failure can also lead to angry customers, which often leads to loss of revenue.
Thankfully, by getting to know the symptoms of network failures, you can take action to solve these problems. So, let's take a look at the most common causes of network downtime:
While some companies use math to estimate fuel levels based on average fuel consumption, this isn't the best option. It's only an estimate and does not factor in possible leaks.
Do you have multiple propane tanks as back-up power sources at your remote sites? If you do, you know how difficult it is to manage all the tanks, along with all your other mission-critical equipment. Proper propane tank management and monitoring is an essential step to ensure your sites are fully equipped in case of a commercial power failure.
A floating sensor may be all you need for low fuel alerts. However, if propane is your main fuel source, you'll likely need a more advanced analog sensor that can track usage rates. Both types of propane tanks sensors allow you to order more propane for your tank before it runs out.
What if you have backup generators to avoid downtime when there's a commercial power outage? This is a good resource. However, what happens when your generator runs out of fuel? Not only does your site lose power, but your generator motor burns up from running on empty.
Damage caused by generators running on empty can be devastating to your equipment. Motors that run on empty burn up and typically the damage is irreversible, forcing you to buy new, expensive equipment.
Adding a simple on/off monitoring tool to a generator helps you avoid preventable equipment damage and keeps your network online.
Your battery plants are a critical component of your network. If commercial power goes out, the backup batteries ensure that critical equipment keeps running.
However, what happens if your batteries deplete before commercial power is back on?
You need the life span of your batteries to be as long as possible. Draining them completely not only shuts down your site but also significantly reduces the total lifespan of that battery. Low voltage can even damage some equipment.
Therefore, it's critical to monitor the current charge level in your batteries. When necessary, you must also reduce the load on them to extend their run time. So, how do you extend the discharge time of your batteries?
Backup to your backup
You may also have a backup generator in case your batteries fail. This is a great idea, but as I said before, generators require fuel to operate. So monitoring the fuel levels is extremely important.
Having an RTU (Remote Telemetry Unit) that sends you alerts is a tool to monitor your equipment and to know when something is wrong. You could use an alarm to monitor the battery charge level. However, that only solves half of the problem.
You have to be able to fix the problem in a timely manner as well. While alarms are great for notifying you or your techs that the battery charge is low, alarms can't do anything to fix the situation. This means that you have to have someone ready to receive an alarm and react at all times.
Power Distribution Units (PDUs)
A >PDU device that allows you to remotely cut power to your devices from your central or home office. These devices are helpful when you are trying to reduce the load on your batteries. They allow you to remotely turn off less-critical devices and conserve more power for mission-critical gear.
While PDUs are extremely helpful for power-cycling your equipment, most are not able to respond to a power loss event automatically. This means that a technician will have to manually toggle buttons in an interface in order to turn units off. Also, there are usually no analogs on a PDU to notify you of the remaining charge of your batteries.
To really extend the charge of your batteries during an outage, you need a device that will systematically and automatically shut down less crucial devices when your batteries hit a critical low. While a PDU is a step in the right direction, your system should also include automated, intelligent decision making.
So, imagine a system with a PDU-like device with an RTUs ability to monitor battery voltage. This would allow your system to track battery charge and automatically power down devices at key battery thresholds. This system will lighten the load on your whole team by automating several processes that previously required human involvement.
With a Remote Power Switch device, this is a possibility. It combines PDU power-cycling with RTU functionality to provide you a solution to battery power draining. By using analogs to measure battery voltage, the Remote Power Switch can systematically determine when to power down your less critical devices. This helps extend the charge on the battery to ensure that your most mission-critical equipment stays running for the duration of an outage.
When a network outage happens, equipment damage might be the root cause.
Many remote sites house tons of expensive mission-critical equipment. Most of these sites will eventually face some sort of environmental emergency. Imagine the devastating effects of overheating or water damage to all of this valuable equipment. If you leave your network unmonitored, you're setting yourself up for unnecessary risk of an outage due to equipment damage.
With the right remote site monitoring equipment in place, you'll be prepared the next time you're equipment faces a threat.
The following are the 4 most common environmental threats that you need to protect your gear against.
This is by far the most common risk at remote sites. IT equipment is designed to operate in a controlled range of temperatures. When it gets too hot, this equipment is at risk of a thermal shutdown (at least) or permanent damage (at worst).
With the right monitoring technology, you'll receive alerts when the temperature begins to rise - so you can quickly respond. Having a quick response is the difference between network downtime and smooth operation.
Excess humidity can cause the internal components of your equipment to rust and degrade - with the potential of short-circuiting. Very low humidity can also seriously damage equipment. That's why it's critical to keep the humidity at a moderate level. You should have an environmental monitoring system that can notify you when the humidity is too high or too low, so you don't leave your equipment vulnerable to serious damage.
Leaking water, just like humidity, can cause serious damage to your site. If water is present around your valuable IT equipment, you need to know. Water damage to your equipment is easily prevented - as long as you're warned about its presence in time. Having the right water leak monitoring technology will alert you of the presence of water so you can prevent serious damage.
Walking into your remote site can be like walking into a furnace. With more powerful processors being packed into smaller units, your equipment generates more heat than ever before. One of the toughest challenges facing operators is cooling all of this equipment.
One of the most efficient ways to cool your equipment is to design a system that optimally circulates the airflow around your equipment. This is why it's crucial to have airflow sensors in place - so you'll be the first to know if something is disrupting airflow to your equipment.
Other than hardware failures, LAN failures are also a common network error. If you have revenue-generating equipment connected to a router, and if you have no visibility of the condition of the LAN, you have no way of knowing your vital equipment is offline.
Most RTUs offer only limited functions for detecting LAN connectivity. A standard remote can only detect whether its local connection is up. If the local connection is intact, but somewhere beyond this connection the network is down, the basic remote will still report a working LAN.
To solve the issue, it's important to also have a dial-up connection for your remotes. A primary and secondary dial-up path will give you visibility of your remote sites when LAN access is unavailable. A primary and secondary dial-up path will give you visibility of your remote sites when LAN access is unavailable.
Get an RTU that is mainly a LAN-based remote, but also has an internal 33.6K modem, which can be used as a primary or secondary connection path.
A good example of an RTU that meets these criteria is the NetGuardian 832A. One of the great things about this remote is that it's a LAN-based RTU that's still operational when the LAN is down. The NetGuardian 832A ‘s internal modem and paging capability, ensure that it always has an alternate path to report critical alarm information.
This means that the NetGuardian can effectively monitor its own LAN connection. Many users have configured their NetGuardians to send a pager if the LAN connection fails.
Natural disasters can also be lead to common network issues. So, having a network management system can help you avoid potential network problems.
However, how do you protect your gear against natural disasters? If you plan ahead, you can at least limit the damage that a natural disaster will cause - and improve your recovery time from the event significantly.
The problem is that natural disasters are unpredictable. The key then is to always be prepared. Having a real disaster recovery plan is the best way to prepare.
Your disaster plan should include:
With each piece of gear you tie into a network fault monitoring system, you improve your situational awareness. Also, make sure you're monitoring battery voltages and generator fuel levels. When a natural disaster happens, you're probably going to lose commercial power at many of your sites. If you know precisely how much backup power you have, you can use your technicians in the best way possible, prioritizing the sites that need fuel first.
Knowing what could go wrong and working out a priority list for fixing downed equipment will help you send technicians to the right sites, with the right equipment, in the right order, when disaster actually strikes.
Are your spares already databased with the appropriate information? Do you need to set jumpers on your analogs to measure current? Make sure you have a documented plan for setting up equipment quickly and ensure that it's accessible (via IP preferably), so if something goes wrong, your people will know just what to do to get it fixed.
Keep an inventory allows you to get your network back online without having to wait for a shipment. If your network covers a large territory, consider employing local parts depots, so your spares can get from storage to site quickly.
In too many networks, the only data path for transporting network fault management information is the network being monitored, When that network fails, you're stuck without the information you need to intelligently dispatch your technicians to get it fixed. An alternate data path ensures you can still get the information you need to fix your troubled network.
With that, if your network suffers an outage, you waste no time getting a hold of network administrators to help you get back online.
The bottom line is that by knowing what the main causes of network downtime many of them can be prevented.
The way to do this is by monitoring your vital equipment. However, you can't trust just any remote monitoring systems manufacturer with the safety of your most important gear. You need a company that is reliable with years of experience. A company that can support open protocols as well as legacy/proprietary protocols so that you can seamlessly integrate your old and new equipment.
We have all the experience and equipment you need to ensure that your network is operational, even when you aren't there. We offer perfect-fit solutions that are sure to help you prevent network downtime.
It is not worth leaving your telecom system at risk any longer. If you want to know more about our network devices and how you can better prevent and avoid network failures, simply give us a call and we'll be happy to help you.
Sensors will allow important data to be gathered, then forwarded to you by a remote telemetry unit (RTU). So, having the right sensors for your scenario is the first step for an efficient monitoring system.
SCADA systems give you reliable remote site information that will ultimately improve your bottom line. Learn how to optimize your data collection with efficient SCADA elements.
Learn how RTUs can help remotely monitor and maintain an equal amount of propane in all your tanks, facilitating vaporization.
You need to see DPS gear in action. Get a live demo with our engineers.
Have a specific question? Ask our team of expert engineers and get a specific answer!
Sign up for the next DPS Factory Training!
Whether you're new to our equipment or you've used it for years, DPS factory training is the best way to get more from your monitoring.Reserve Your Seat Today